fabricated out of 16/14 S.W.G.,C.R.C.
sheet, duly printed with hard drying
synthetic enamel over a coat of metal
primer dust and vermin prove, having all
components duly wired with copper wire,
Besides Automatic Starting & Stopping
of Engine on Power failure & restoration
the AMF is capable of scanning the State
Electricity Board supply for low and high
voltage and allow the same to the consumers
being within a healthy band and cut offthe supply if not usable, wait and
power failure or cut off, to automatically trigger.
The Generator, three starting attempts are made in Case generator does not start
in the first attempt while the starting signal seizes on generator starting by itself,
on failure after three attempts an audio visual signal is flashed.
After starting few seconds are allowed to build up and on confirmation of healthy
voltage supply from generator it is connected to the consumers. On restoration
and confirmation of healthy supply from State elect. Board confirmation is made
for consumer’ compatibility before disconnecting generator supply and while
giving rest time to consumer Appliances State electricity boards supply is
restored so as to avoid spikes. Providing healthy idle time generator is brought
to rest automatically while the entire system is re-set to take next starting signal as
and when required.
MBS/MBD Motor Control Centres (MCC) are of bolted construction
The metal enclosed switchgear
panels, the requirements of medium voltage system for indoor application
as IEC 298/IS3427.